Standpipe and Fire Pump Inspection & Service
Standpipe and fire pump systems are required to be maintained and inspected monthly, quarterly and annually in accordance with NFPA 25. Flow tests of wet standpipe systems shall be performed every 5 years. Dry standpipes are required to be hydrostatically tested every 5 years. Records must be kept by the building owner or manager for examination by the insuring agent and/or the authority having jurisdiction.